London Data Center Specifications
Two vacant, one shell
Two geographically separate sub stations (dual feed) with contracted power of 17MVA and 4.5MVA
17MVA Capacity at N + 1 served by 2 x incoming feeders each rated at 8.5MVA
(2) occupied halls served via 4 No. UPS substations arranged in pairs, each pair (input and output substation)comprise 2x 5No 500KW rotary type UPS modules in 2(N+1) configuration, with 5 minute battery back-up.
4.8MVA Capacity at N + 1 served by 2 x feeders each rated at 2.4MVA
2No. modular UPS systems (A and B side with each module comprising 6 x 200KW at N +1) operating in 2(N+1) configuration.
20+ Fiber Carriers on-net and near-net
Frontier, AT&T, InnerCity Fiber, Zayo, Lumen, Verizon, Crown Castle
4,831m2 [52,000 sq ft] data center footprint
Spare capacity of 2.6MW of available cooling (assuming N+20% on two occupied halls).1,000mm Raised Floor
Ground Floor 10,153.5 sq m [109,291sq ft] First Floor Office 166.9 sq m [1,796 sq ft] North Mezzanine 1,335.8 sq m [14,378 sq ft] South Mezzanine 1,528.3 sq m [16,450 sq ft] Roof Plant 334.9 sq m [3,605 sq ft] Total 13,519.4m2 [145,520 sq ft]
External Security: Site secured by 3m paladin and galvanised steel palisade fencing with access via man traps and vehicle holding bay with electric sliding gates and manned security hut
Site full monitored by CCTV with onsite 24/7/365 security
Internal Security: Man Traps anKey Card System with Reception and Manned Security 24/7/365 security
VESDA double Knock gas fire suppression system
Main Facility: Two separate chilled water systems providing final cooling via CRAH units. System designed to provide 2(N+1) with each set of chillers consisting of 6 chillers, each rated at 1266KW, providing separate high and low system. Pair of primary chilled water pumps fitted to each chiller. Each system has 2x40m3 buffer tanks.
DKW Hall: DX system with CRAC units installed in service corridor, with external condensers.